It looks like I don't have single point grounding at my house. The main disconnect box on the back of my house is tied to a ground rod while the breaker box is connected to the water pipe. I guess that violates code? I suppose I should hire a licensed electrician to check things out and, if necessary, bring the grounding up to code. I have my new dish grounded to the same ground rod as the main breaker box, though.